Multiple-conductor cable using non-integral jacket
105 deg C, 600 or 1000 Vac, Cable flame.
40 AWG minimum.
Labeled or complying with manufacturer's AWM Procedure.
Two or more conductors or groups of conductors laid parallel or twisted forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. May use same or mixed AWG size.
Optional, Extruded PVC, 6 mils minimum thickness at any point.